For ceiling installation
Joint support for installation in ceiling is used with screw, pendelum or wire and must be centrated over each joint of the power track.
Bracket for ceiling must be used in every end of a power track and where an additional fixing point is necessary. Max. length between
brackets is 1200 mm. The brackets are clipped on the power tracks/cable ducts and locked with the locking screw.
Max weight between two fixing points are 15 kg.
Art no 4399 and 9655 have press nut M10 for threaded bar and are used by pendelum installatiton and by installation together with cable basket.